Importance of Filtration for Process Water & Wastewater Reuse
Views : 776
Update time : 2021-03-15 15:29:42
Filtration is very important for many commercial/industrial process water & wastewater reuse applications. In reality, pumping wastewater from somewhere like a refinery, food/beverage, textile, or oil-produced water application requires pre-filtration due to the high amount of suspended solids in these typical applications. In fact, there are typically several filtration and treatment steps in these applications to ensure that the treated water meets the required discharge or reuse standard. In addition, filtration in water treatment ensures reduced operating costs on downstream polishing water treatment systems.
There are a few examples of advanced treatment processes that need prior filtration for successful operation:
1. Finer filtration
This includes membrane filters like reverse osmosis filters, ultrafiltration, micro- or nanofiltration as well as any finer media filters or nano cartridge filters. Most filtration systems operate on a gradient. They start out with a rough, coarse filtration and move along in steps to the finest level necessary.
This process of course to fine filtration is designed to keep the filters going for as long as possible before they need cleaning, backwashing or replacement. If you have a mixture of clay, silt, and sand suspended in a solution and immediately try to filter it through a nano filter, it’s going to clog up quite quickly. However, if you filter this solution through a filter that will catch all the sand first, then one to catch the silt and clay, your fine filter will be able to optimally operate by handling the smaller particles.
Also, the pressure is something to consider. Unless a filter works by way of gravity, it likely uses a pressure system to force everything through the filtration medium. These filtration systems are designed to operate under a certain pressure range, but as the filter medium gathers particulates, the system experiences increased head loss, where the pressure difference is so great that the pumps are working less efficiently, and a backwash cycle is initiated to prevent the possibility of a particulate breakthrough in the filtered water.
Disinfection systems involve the treatment of microscopic pathogens by way of oxidation. However, interference due to particulate matter decreases the treatment efficiency of this unit.
For instance, UV disinfection uses ultraviolet radiation to destroy bacteria. The wavelength of the light travels from the light source through the fluid to the targeted contaminants. However, if suspended particles are within the influent, they will physically block the light waves from reaching the pollutants that need to be disinfected appropriately.
3. Advanced Oxidation
Similar to disinfection, advanced oxidation operates dissolved compounds. It uses hydroxyl radicals produced through a combination of ozone, hydrogen peroxide, UV light or electro oxidation systems. Unfiltered contaminants prevent the effectiveness of the UV light as described above. However, other contaminants, called hydroxyl scavengers, will also reduce process efficiency if they are present in a high enough concentration. These scavengers have an affinity for the hydroxyl radicals and will sweep in and react with them before the targeted compounds are destroyed. However, proper pre-filtration along (with some other treatments) can keep them out entirely.
Whether it's a chemical or electrochemical coagulation system, a certain level of pre-filtration is key to effective treatment. Coagulation systems are typically used to coagulate and flocculate smaller particles that don’t settle out very quickly or efficiently. The addition of chemical additives or electrical current is what drives the process. However, these processes typically work best at a particular concentration range for the target constituents. Filtering out larger particles prior to these systems will ensure that these systems work at their maximum efficiency. In addition, higher concentrations of suspended particles would require adding more chemicals or supplying more voltage to the system to operate effectively. To reduce operating costs, filtration in water treatment is advisable.
As we all know, filtration is so important for water/wastewater treatment, so we also need the filter element/strainer, such as the wedge wire screen used for the industrial filtration system. We supplied the wedge wire screen and stainless steel filter element for different industries, welcome contact us to get more.